Country ref. 01008795
Up to 24kV
StandardsNational : NF C 33-001
Joint between :
- 3 single core synthetic insulated MV cables
- 3 single core synthetic insulated MV cables and 3 single core paper insulated MV cables
- 3 single core paper insulated MV cables.
Cable specifications :
- UTE C 33-223
- NF C 33-220 (HN 33-S-22)
- NF C 33-223 (HN 33-S-23)
- NF C 33-100
- Section : from 50 to 240 mm².
Meets the NF C 33-001 test standard.
Each conditioning contains the necessary to make a three core joint as well as detailled fitting instructions.
The connection bushings (type RJ) are to be supplied separately (see Connections for joints/branch joints).
For the resin injection in case of a pump injection, use an injection tool (see Accessories for joints/branch joints).
|Conductor material||Copper or Aluminum|
|Conductor cross-section, range||95 .. 240mm²|
|Rated Voltage Uo/U (Um)||12 / 20 (24) kV|
|Dielectric withstand voltage, 50Hz 1mn||55kV|
|Ambient installation temperature, range||5 .. 40°C|