Country ref. Codet Enedis : 67 92 801
StandardsNational : C 33-052;NF C 33-001
Indoor connection for synthetic insulated cables and especially on UTE C 33-223, NF C 33-223, NF C 33-220 cables of sections 50 to 240 mm² and of voltage 12/20 (24) kV.
Meets the following standards :
- NF C 33-052
- NF C 33-001
Each conditioning includes detailled instructions about the cable preparation, as well as the placing of the sealing ends by simple extraction of the support tubes.
This technology does not need a source of heat nor filling or wrapping material.
The sealing end can be powered-up immediately after its connection.
Type C AU terminal lug is to be supplied separately (see ''Connections for LV and MV sealing ends" ).
|Conductor material||Copper or Aluminum|
|Conductor cross-section, range||50 .. 240mm²|
|Rated Voltage Uo/U (Um)||12 / 20 (24) kV|
|Maximal partial discharge at 2Uo||21pC|
|Dielectric withstand voltage, 50Hz 1mn||55kV|
|Ambient installation temperature, range||5 .. 40°C|
|Main cable||Synthetic insulated cable|