Country ref. Codet Enedis : 67 92 803
StandardsNational : C 33-052;NF C 33-001
Outdoor connection in polluted zone for synthetic insulated cables and especially on C 33-226, UTE C 33-223, NF C 33-223 and NF C 33-220 cables of section 50 to 240 mm² and of voltage 12/20 (24) kV .
Meets the following standards :
- NF C 33-052
- NF C 33-001
Each conditioning includes detailled instructions on the cable preparation as well as the placing of the terminations by simple extraction of the support tubes.
This technology does not need a source of heat nor filling or wrapping material.
The termination can be powered-up immediately after its connection.
The type CA lug is to be supplied separately.
|Conductor cross-section, range||50 .. 240mm²|
|Rated Voltage Uo/U (Um)||12 / 20 (24) kV|
|Maximal partial discharge at 2Uo||21pC|
|Dielectric withstand voltage, 50Hz 1mn||55kV|
|Ambient installation temperature, range||5 .. 40°C|
|Main cable||Synthetic insulated cable|